Fellow InterNACHI members,
I recently performed a home inspection. During my visual inspection of the electrical panel with the cover removed I noticed the following:
- Two or three wires connected together on the bus bar under the same screw
*neutral and ground wires connected together under the same screw on the bus bar
My comments on the report were as follows:
Recommend further evaluation by a licensed electrician as one or more neutral wires and ground wires at the main electric panel should be serviced. Unless the manufacturer states otherwise, bus bars are only designed for one current carrying conductor per terminating screw.
The Realtor later informed me that an electrician was called and he stated that there was absolutely nothing wrong with that wiring installation in that electric box. Now I am labeled as not knowing anything related to the electrical system in a home. Is there a proper reporting procedure for something like this.
Javier Mojica NACHI17031306