Today’s inspection had this 200 amp panel. The left side is the neutral bus bar which is bonded. The bus bar on the right was not bonded and/or floating with both neutrals and grounds connected. At the bottom right, is a grounding bus bar, with grounds only, which was bonded. Now, all neutrals & grounds, at the main panel, need to be connected/on the same bus bar which is bonded to the enclosure, right? (or all grounds & neutrals need to connected and bonded to the enclosure) I realize the pic is a little difficult to see, but that’s all I have. Any help would be appreciated.