Ahh…found the topic…here you go thomas
Quote from the MOD on that site :
The hole is for the gec, some inspectors call it out due to lack of training and reading other posts. I guess, apperantly) some ahj requires it as well.
Thx paul, was reading another thread here, and found a thread elsewhere http://electrical-contractor.net/ubb/Forum1/HTML/001686.html
P.S. there seems to be a member named: **PAbernathy **who jumped in on the thread. I wonder who that is.
Yep…thats the one I posted as well…make sure you read all 3 pages of the responses…
Ok…Example of KO for GEC…Shown Below
Example of a WEEP hole within an enclosure- shown below
Also example of a tapcon being used. lol
good observation their Ben…Me simply LOVE’s them TAPCONS
Not sure…but I HEAR he is a real A$$hole…probably true…