Originally Posted By: Russell Frame
This post was automatically imported from our archived forum.
Had the power company out to take a look at my prep for a hookup, he had a couple small things he wanted changed.
One I really dont get.
I have my main panel grounded to the rod, as one would expect. I also have the ground lug in the meter box grounded. This is normal per all the drawings I have seen. But the installer said I had to take out the meter grounding connection.
Am I wrong that the meter isn't normally grounded? If not why is there a box grounding lug?