There was a bank of main disconnects (3) outside this commercial building. The disconnect pictured has a convenience outlet attached to it. The conductors share the same conduit as the distribution side of the disconnect. The service side comes from a trough mounted below the disconnects. Is this okay to share the raceway like that?
Also, the neutrals are not bonded to the cabinets in any of these.