When the discharge pipe is Horizontal is there a minimum distance before a 90? And is there a limit of how many 90’s on a single discharge pipe? Please see photo! Thanks in advance
As long as it flows by gravity .
Excessive length over 30’ (9.14m), or use of more than four elbows or reducing discharge line size
will cause a restriction and reduce the discharge capacity of the valve**
Temperature and Pressure (T&P) relief valves - Support - Water Safety & Flow Control -Watts
Gee-zus I can’t see thru all that mess but don’t see bonding
Boss said “use as many fittings as possible we charge by the foot and fitting”