56 year old home
Upgraded electrical system.
100 Amp Meter (listed as 15 Amp which was the test rating),
200 Amp Main Disconnect.
I will identify the Service Size as 100 Amps. This is sufficient for this home since it has no Air Cond, an all gas range, one electric water heater and one gas water heater, electric dryer, no pool, no spa, no whirlpool, gas furnace.
**The question is… **does the 100 Amp meter **actually restrict **the service to no more than 100 Amps?
Also, the bus bars to the main disconnect appear to be aluminum but I didn’t find any cu/al rating on the main disconnect. The panel is rated for use with aluminum but I didn’t see any markings on the main disconnect indicating it was also rated for Al. Some of the smaller breakers in the panel did indicate cu/al but they all had cu conductors.
Second question is… is the panel rating enough for it to be considered okay to have the aluminum connections? Or does the breaker need to indicate it as well?