Client commented that light bulbs didn’t last too long.
Upon arrival at inspection property, I noted that utility cable’s neutral was severed due to a fallen tree.
Receptacles inside home tested 240V, lights were burning bright…
Electric baseboard heaters appears to function properly.
A severed neutral from the utility cable should not cause a 120v receptacle to test 240v…
Question is what would cause 120v circuits to test 240v?
Thanks in advance for your response!