I wanted to post this to see what others say.
Main disconnect located in garage. 125 amps.
Sub(remote distribution panel) located in basement with a 200 amp breaker. SEC was rated for 125 amps.
Q1) What is the service size 125 or 200 amps?
Q2) Is the 200 amp breaker acceptable in this application, are the SEC properly sized?
Q3) Seperate question
What are your thoughts on the split bolt connection for the GEC? Looks like a crappy connection, could we not just go to the available bar on the panel? This connects to the sub
Q4) I know the bonding screw needs to be removed at the sub, but is it acceptable to be there and not be in contact with the panel?
I now know the answer thanks to my friend Jeff Pope. (You are a good man to answer my calls)
I should post the other question to I had on the Bonding jumper to the grounding terminal.
I would of mis reported both if I had not talked to Jeff.