Question on installing the electrical service conductor to my 240 vac air compressor.
The compressor will be installed in a detached outbuilding, which has a 100 amp “distribution” panel (sub panel from the homes’ main panel.)
It has a floating ground neutral, meaning the ground buss and neutral buss are seperate, the way they should be.
So my question is this: If the 20 amp, 240 vac, 12-2 conductor has two ungrounded conductors (black & white), the ground then is attached to the ground buss …or the neutral buss?
I think Paul A. will know the answer on this one.
Thanks in advance