Originally Posted By: jpope
This post was automatically imported from our archived forum.
I was told in a different thread that Texas inspectors are required (by the State) to remove a relative sample of cover plates to confirm proper application of AL/CU receptacles and/or "pigtailed" connections whenever they see AL wire in the branch circuits of a service panel.
So what is required in a case when there is a mix such as the pictures below? How do you limit your liability in a case like this?
Curious in California
JPI Home Inspection Service
"At JPI, we'll help you look better"