Originally Posted By: roconnor
This post was automatically imported from our archived forum.
Not sure what ya mean by hardwired “together”, but appliances that draw more than 300 watts (about 3A at 120V) must have a means to disconnect the supply power within sight … which can be an accessible plug or a switch ahead of the appliance, or a switch on the appliance marked “Off” that cuts power.
Look at NEC Article 422, or If ya have a copy of the IRC look at "Table E4001.5 - Disconnecting Means" ... its a pretty handy summary of the requirements ... ![icon_wink.gif](upload://ssT9V5t45yjlgXqiFRXL04eXtqw.gif)
Robert O'Connor, PE
Eagle Engineering ?
Eagle Eye Inspections ?
NACHI Education Committee
I am absolutely amazed sometimes by how much thought goes into doing things wrong