Here is a spa disconnect like I have not yet seen.
There was a 20-amp GFCI breaker with a 30-amp GFCI breaker next to it. The 30 had a sticker over the test button stating that the spa’s neutral wire was connected to that breaker. However upon examination the spa neutral appeared to be connected to the 20-amp GFCI.
What am I seeing here? Why two GFCI’s in one disconnect box? Is there something special about the spa?