Originally Posted By: pmorgenstern
This post was automatically imported from our archived forum.
Hi, I’m new to this forum but a member of NACHI. Today I inspected an older home that had been renovated and had several additions added on and 150 amp service that had been installed prior to the renovation and additions.
After the additions had been inspected by the building dept, a new stone fireplace was installed. In doing this, the mason covered the service wire from the meter to the main panel for about 6’. No conduit.
Is this a problem?? Somehow it doesn’t seem kosher to me. If it is not right, is it a code violation?? The inspection was conducted in New York.
Thanks for your help