Is there a reason to flag the following:
Work shop garage
- Garage Sub Panel
- Panel has main shut off, 3 220 circuits for individual tools and
several 15 amp receptacles
- Panel has grounds isolated and ground bar in the ground.
I thought it was a good idea on the six throws idea
Main Panel is on the other end of the house.
Question: I thought it was unusual for a Sub Panel to have a main breaker.
Am I correct in assuming that the panel is fine provided the grounds are isolated and grounded?
Tilley Home Inspection