Originally Posted By: mcameron
This post was automatically imported from our archived forum.
This brand new house only had one panel in the garage. It had a 200 Amp main breaker and the rest of the houses breakers were under the main. The grounds and the nuetrals were on seperate bus bars. The grounds were bonded, but the neutrals were not. Please let me know if this should be considered a sub or service and if the neutrals and grounds should be on the same bus bar and/or bonded together to the box. I also could not find the main grounding wiring, should I assume it is a UFER? Thanks.