I inspected a condo a couple weeks ago. I called out the electric panel for not having any grounding/bonding to the panel. I understand if it is wired as a remote panel the neutrals would be isolated from the panel but the grounds would still be bonded. There was no grounding screw or strap.
An electrician came out and said it was fine that the condos are wired like this.
On the exterior, there was one disconnect - not sure which condo it was for.
If it is ok not to bond the grounds please explain.
Sorry I can’t get anymore pic to load right now.