Have a home that was found to have quite a bit of knob and tube wiring in the attic and going down into the walls. Panel has been replaced and upgraded but all outlets are ungrounded (3 slot).
Home is going to be used as a nursery school. I reported the wiring suspect and included all the usual issues with knob and tube and recommended that an electrician be consulted to check the wiring issue and likely to do a upgrade if he felt it would be needed.
The electrician says that it is perfectly safe with nothing to worry about.
My clients now think I misled them. Am I missing something? I see a lot of this wiring and always report it this way. I could really use some advice.
LSBHI License #10518
New Orleans, LA