The main was installed in a closet. I had my client try to reach the main breaker.
As you can see that the panel is installed to high.
The panel is a recent install. The home is a slab.
What is the height requirment and panel are not allowed in closets correct?
Max height of breakers: 6’ 7"
Provide working space: 30" min side to side - 36" min in front
The 30" is not side to side, but overall (the dimension does not have to be centered on the panel).
. . .and can’t be located in a clothes closet.
How about this one?
I see those occasionally. I just can’t understand what the were thinking (or if they were thinking at all).
Oops…thats what I should have said!