Originally Posted By: jpope
This post was automatically imported from our archived forum.
I don’t normally pull covers at the meter pan. This one just fell off when I opened the cover.
Call me stupid, but this looks like it has 240 volts to each pole. Can it be?
Let me see if I can explain the picture.
It's an under ground service to the meter with a 50 amp, two pole (240V) breaker. From there, it exits out the bottom at the black plug (which is actually a standard 240V plug) to a mobile home.
Can someone 'splain ![icon_confused.gif](upload://qv5zppiN69qCk2Y6JzaFYhrff8S.gif)
JPI Home Inspection Service
"At JPI, we'll help you look better"