Gee I wonder why the ceiling had been repaired under this area?
That kink is not too good for the system either.
Good eye Bruce.
wow!!! continues to amaze me on what we find as inspectors. Good job Bruce!!
hope you called out to replaced that kinked line also.
Oh,*** that ***missing insulation.
This is the second time I have found this in the same city must be the same installer??? How would you handle this item.