Saw a 1/0 Al se conductor feeding into a main service panel with 150 amp breaker this morning. It was a 4 pt ins. inspection. How would you word it for the insurance people?
“Main breaker too large to prevent adequate overload protection for service entrance wiring. Recommend a licensed electrician evaluate and repair”?
Update: This has been resolved.