Originally Posted By: jmyers
This post was automatically imported from our archived forum.
I would not doubt what you are saying at all. It looks to me like there are several more neutral wires on the bars then there are grounding wires. Most likely they took the two prong receptacles and replaced them with three prong and left them ungrounded.
I believe I can see a bonding wire with white tape running from the ground bar to the neutral bar. I think that is a ground wire running from the bottom bar but it was difficult tell where it terminates, if indeed it is a grounding wire. If that is the grounding wire, where is the bonding wire?
If you had pulled one of those plates off the open ground receptacles I believe you would have found that the grounding wire was missing.