A 90-amp twin breaker fed an HVAC unit of the roof of this condo. The two hots were connected to the breakers in this sub panel. The neutral was not connected to the neutral bus bar. An equipment grounding conductor from that cable was connected to the ground bus. Is the ground carrying the return of the circuit? Doesn’t seem right.