Originally Posted By: cbottger
This post was automatically imported from our archived forum.
I do realize HI’s do not include trouble shooting within the scope of an inspection, but perhaps there are other people like me than just can not stand not to know Why something is not working the way it is designed to operate Thus I am going to ask a trouble shooting type of question. Its late so will make it brief.
When operating an A/C unit and the TD is say 5 degrees and the suction line or the big line is very warm to the touch and the unit has been operating for approximately 15 minutes what would be the most probably cause of failure to have a proper TD. ONE STAR FOR THE CORRECT ANSWER ![icon_wink.gif](upload://ssT9V5t45yjlgXqiFRXL04eXtqw.gif)
Don't argue with an idiot someone watching may not be able to tell the difference.