Originally Posted By: Gino Conner
This post was automatically imported from our archived forum.
Just to expound a little on what Gerry said and for the info of others.
qualifies these receptacles a little further on islands and peninsulas. The receptacle pictured appears fine, but it could not have been more than 12 inches below the counter. Also, if there were more than 6 inches of counter overhang or
a cabinet hanging above it at a height of 20 inches or less, the receptacle would not be allowed at all on the side. ![icon_cool.gif](upload://oPnLkqdJc33Dyf2uA3TQwRkfhwd.gif)