I thought that the service entry cables if marked 200 amps must match the main breaker at 200 amps as well. I read today that was wrong. I read today that if service entry cables were rated at 200 it is OK for the breaker to be rated at 100. Which is correct?
Didn’t you ask a similar question in this other thread? That other thread has two responses, did you have a chance to read them?