Please tell me what you think about the service size for this house. It is 120/240 service drop. It is a smaller meter, but has listed 200cl on it. The SE conductors appear to be #2 AWG AL. The main panel (Cutler Hammer) is rated for 125 amps. There are 5 main disconnects that total 190 amps. 1969 house.
Also, what do you think about the black wire lugged with the ground at the bottom right of the main panel? And, also about the ground lugged with the neutrals on the neutral bus in the sub panel? Thanks in advance.