…at figuring this one out. I have no idea and just referred it to an electrician.
I would love to hear your ideas on why I would get a 30 volt reading between the neutral and the ground. Comes off a subpanel with neutral/grounds connected, house is occupied. No other info available.
So I’ve been looking up the ghost voltage and came across this. I assume since I was in the garage on the concrete floor I was a big human capacitor. I initially had my tick tracer out and it went off within 6" of the receptacle, that’s why I checked the voltage.
Mike L. or Mike W. am I correct in thinking that if I had the multimeter attached and then I connected the Wiggy, the voltage reading would disappear?