Originally Posted By: jpope
This post was automatically imported from our archived forum.
I?ve never seen this done before. A terminal bar was added into this junction box for the EGC?s and neutrals. If this neutral bus was isolated form the enclosure, would this setup be allowed?
I don?t see an issue with the terminal bar for the EGC?s, but what kind of problems might the neutral bar create other than the potential for possibly unbalanced loads on the neutral conductors back to the panel board?
Any NEC references (for or against) would be appreciated.