Originally Posted By: Brian A. Goodman
This post was automatically imported from our archived forum.
Hi Joe. For some reason I never find all of the stuff in these things, but I’ll take a run at it anyway.
I see a 200 amp main for a 40 circuit GE panel.
I see what is almost certainly an aluminum neutral, which someone bothered to install with contact paste (I'd be checking the hots next).
I'm pretty sure I see more than one neutral per terminal on the neutral bars, as well as neutrals and grounds mixed in the same terminals (neither is allowed).
I see that the enclosure is bonded.
I see that the wiring is not a God-awful mess.
I can't be certain, but it appears that the main is tripped. If so you have to wonder why.
I should probably be saying "grounded conductor" instead neutral, but I think that term confuses a lot of people, so I don't use it much.