I am still training to become a home inspector… Electrical is definitely my weakness. I inspected a 1985 house for a friend. This is the main house panel. Double tapping on the neutral should be called out correct?
The shop had 2 small panels in it with tons of issues. But both looked like the ground and neutral bars were bonded. Am I seeing that right? I am trying to be able to understand how the bonding works in different panels and be able to spot it confidently. The stranded copper wire feeding the 100 amps seemed too small to me as well. I will definitely need to carry a wire gauge with me. It was a great learning experience!