Hey guys, will you give me a little help on this panel set-up. It’s a 100 Amp Square D panel. The potential issues I see are:
[li]Double-tap on main[LIST=1][/li][li]The double-taps go to the panel on the right with a breaker for the AC. Since they go to a breaker is that okay?[/li][/ol]
[li]Double-taps on breakers[/li][li]Grounded conductor’s (neutrals) on same fasteners?[/li][li]Grounded conductor from service panel is a bare copper conductor?[ol][/li][li]Haven’t seen that one before so wanted to make sure.[/li][/ol]
[/LIST]Anything else I’m missing?