Originally Posted By: anatol polillo
This post was automatically imported from our archived forum.
Inspected a townhouse today. 5 years old. The service panel was fine, except for the dryer circuit, AL with no anit-oxidant at breaker. Square D, so that might not be a problem. The ground to the copper water supply was AL. It had the paste in the box, but not where it was attached to the copper main water supply. I did not write it up, but it seems that if it has it in the box, it should have it at the other end of the connection. Am I out of my mind???