Lender called and asked me to look at a newer Home Inspectors Report AND the Repair Electricians Report … They said
- Home Inspection Report
The whirlpool either had no visible ground OR no visible bonding wire. Have electrician verify its presence or install one.
An electrician came out and said:
Code requires all metal piping system, metal parts of electrical equipment and pump motors associated with a jacuzzi tub to be bonded not grounded. I observed no metal piping visible from the access door under the jacuzzi and no additional electrical equipment other than the single pump motor and jacuzzi tub faucets , therefore no bonding is necessary and GFCI protection is sufficient.
- Home Inspection Report:
The light switch at the top of the basement stairs turned on the light over the stairs, but the light switch at the foot of the basement stairs did NOT turn on the light over the stairs. It could be defective, a burned out bulb OR the light may not be wired properly. Repair as needed.
The electricians report said:
All lights in basement function with switches. The switch at the bottom of the stair was removed and a blank plate was installed in its place.
Applicable Comments or Thoughts
***the lender has opinions/comments from both parties that actually were on site to postulate their opinions/comments
are you trying to prove something by injecting your opinion or requesting of others to step into the crosshairs of something they have no factual knowledge of?
some things to consider based on info provided
jac/spa/pool motors require bonding at the mfr lug connection, absence is a deficiency
covering/omitting a required switch is a deficiency
have fun stroking the lender big guy***