I am in a situation here.
The conductors going into a 30 amp breaker looked to be 12 AWG. Although, it is real hard to confirm without unscrewing it. I compared to my sample 12 AWG and it looks the same but 10 AWG is very close. How should I write this up without making a mistake one way or the other? Thanks