Originally Posted By: mpettitt
This post was automatically imported from our archived forum.
Can anyone give me a clue as to why condensate would be dripping down from the center of the evaporator coil of the air handler. The unit had been running for more than an hour and condensate was observed running out from the exterior drain line (not clogged). The unit is a Rheem 97 model A/C split system and appears in very good condition (no rust). Thanks, Mike