WE JUST HAD A NACHI CHICAGO CLASS ON GAS DELIVERY.
NACHI CHICAGO RULES!!!
So it was too weird that the very next day at my inspection i find this.
I’m thinking this is CSST ( yellow colored pipe going into dirt)
Also note the NON METALLIC CABLE THAT IS BURIED - might be going into that plastic sleeve though i don’t like it anyway. The seller had lots of tools and did a buch to the home- i found lots of not quite right stuff as far ans installation - non pro stuff consistent with a do it yourself, fawk da code attitude.
THIS IS IN CHICAGO
Does this look like CSST to you guys?