I am working on my mock inspections, when I came across an interesting situation. A distribution panel, that I inspected had multiple instances of two neutral conductors (both 14 AWG), on one lug. As listed on the distribution panel label, I read it as allowing two (2) 14 AWG conductors, among other options.
A couple of days ago this house was inspected and called out for this. My question isn’t necessarily to say the inspector wrong. If this was an actual inspection did I make a mistake?