I inspected a house the other day, and I wrote the house up for two grounding conductors under one lug. The homeowner’s son asked how they could do it any other way since there are more grounding conductors than lugs on the panel. There is even some expansion room for additional breakers. So my question is, is this a panel issue? Or should the original electrician have added another bar for the neutrals?