I have to run but I will leave you with this…
1.)Sizing a Panel - http://www.theelectricalguru.com/video.html
2.) Yes, on those breakers call out double taps…keep it simple
3.) Notice the cable on the left side has pulled out of the connector…call that out as it could damage the conductors inside the cable. Probably because NONE of the cables coming into the left or right side of that panel is properly supported and because of that…thus the cable pulling out on the left like it is…can wear away at the insulation on the conductors over time.
4.) If their is no main breaker located at the meter location or somewhere ahead of this panel…call it out as such…but look for the main disconnect possibly at the meter location or the other side of that wall space.
5.) I also know that connector at the TOP is not designed to have all those ROMEX cables going into it…call me FICKLE but I would call that out also as if they are jammed in it could have damaged the cables outer jacket and should be observed for this when you actually did that inspection.
6.) Yes, always call out Rev. Pol and let them deal with it…not calling it out would be the problem ( and I wont go into why…just not anymore )
Hope this helps…gotta run…plane to catch soon.