Roy Cooke this one’s for you since you asked me why I don’t post here very often. I’ve been trying to read more posts and I’ve even learned a few things from Mike Whitt. :mrgreen:
I just inspected a house this evening and the ground wire was disconnected at the water main which obviously goes in the report. No ground rod either. My question is: Why were the 3 pronged receptacles still showing properly grounded when I used my tester? Is the tester picking up the ground connection at the transformer through the neutral conductor?