Here are several pics. from yesterday’s inspection. This inspection took 5 hrs. / long night. I am looking for comments on pics while I try to pull everthing together. Any comments are appreciated.
From left to right: Pic#1 is the main panel in the home, power coming in from the street. This panel has a 200amp SEC and main breaker. Pic#5 is in Pic#1 and I believe its is feeding Pic#2. No bushing or bonding clap for the pipe. Unable to locate ground rods for this panel. Pic#2 is another panel in the home, other side of home. This panel is rated for 150amp. main, but has a 200amp main breaker? Unable to locate EGC for this panel. Pic#3 is located in an detached, garage/apartment building. As you can see it is missing plugs for the knock outs. Also, the grounded and grounding conductors are together. It is also only being fed with a three wire service and there is water and phone to this building. Pic#4 is another out building being feed from Pic#2. There is no EGC/ground rod and the grounded and grounding conductors are not isolated form each other. This panel to is feed with a three wire service.