The home inspected yesterday is in the county, not city. Built in 2005.
Pic 1 - The main power source starts at the meter / pole in the yard. 200 amp CH panel, 200 amp main disconnect
Pic 2 - The second panel is on exterior at the garage. 200 amp CH panel, no main disconnect. 4-wire feed, 10 double pole breakers, bonded, metal bar connects the 2 bus bars
Pic 3 & 4 - The third panel is in garage interior. 200 amp CH panel. 3-wire feed, many breakers, bonded, metal bar connects the 2 bus bars, doubled neutrals. Several things wrong in this panel.
- In this setup, should the second panel contain a main disconnect?
- should it be bonded?
- should the bar be removed between the neutral / ground bus bars?
- does the maximum 6-disconnect rule apply?
Third panel: to work correctly,
- change to 4-wire feed
- remove bar between neutral and grounding bus bars
- remove bonding
- separate neutrals
Anyhow, all info appreciated.