Forgive me, I’m new at two things: home inspection and downloading photos on this forum. Hopefully I got the photos on.
One of them shows the main disconnect, the other is what I believe is a subpanel located inside the home. It is double tapped at the mains and has one aluminum wire connected to a 50amp breaker.
Is double tapping in this case okay or not?