I am a Realtor representing aBuyer who has been going back and forth between their home inspector and the Seller. The inspector called out an issue with a double-tapped breaker. However, the Seller is stating that this particular breaker can be double-tapped. The panel is a made by Square D Company and looks like it says model QOBW (but it’s faded so I can’t really tell what the second letters are) rated for 125 amps. The breakers say LD-955 2 pole. I have seen around the forum that this type of panel does, in fact, accept double-tapped breakers. However, I want to be sure the breakers are properly configured. Can someone tell me if the configuration in the attached picture poses an issue? Thanks!