Originally Posted By: jtedesco
This post was automatically imported from our archived forum.
Look here for the pictures, and other items of use, even taking tests on the NEC!!
Pictures By, Joe Tedesco
Violation #1 - Temporary bulb, shock hazard!
Violation #2 - Keyless lampholder in closet.
Violation #3 - In one receptacle out to the other.
Violation #4 - A well destroyed junction box.
Violation #5 - Non covered, overcrowded, and partially damaged J-box.
Violation #6 - LB totally disconnected from rest of raceway.
Violation #7 - Defective GEC to ground rod.
Violation #8 - Electrical Metallic Tubing (EMT) hanging in the breeze, wires exposed.
Violation #9 - Working clearance problem for disconnect.
Violation #10 - Cord coming out of cord-connected plug.
Violation #11 - Overcrowded junction box in a hospital?
Violation #12 - Damaged junction box in a front lawn.
Violation #13 - Working space violations in a rest home.
Violation #14 - Junction box in an attic with many violations.
Violation #15 - Work done by an Unqualified Person using paper bags?
Violation #16 - Exposed live energized bus in a hotel panelboard.
Violation #17 - Sheet metal screw is no good for EGC, and open KO's.
Violation #18 - Hotlegs, many of them and exposed they are!
Violation #19 - Can you tell what's wrong with this?
Joe Tedesco, NEC Consultant