Originally Posted By: anatol polillo
This post was automatically imported from our archived forum.
Today I saw a new (to me) configuration, sorry no picture, but I will describe it as best I can.
100 amp Main panel Cutler Hammer. The service conductors came in at the bottom and went into a double breaker at the bottom of the panel on the right side, no marking as to size, but seem to take the wire just fine. I normally see the conductors attached to the bus at the top, with the main breaker just below. There were other problems with the wiring in the panel so I recommended Sparky. I have seen split bus boxes before, but this did not look right to me. Any Ideas??