Originally Posted By: dvalley
This post was automatically imported from our archived forum.
I expect you to be the first to answer..but lets see.
I inspected a two-family house today with two individual 100 amp SE panels. One ground wire was installed at the water main. A single ground wire that was attached at the water main was coming from one of the SE panels. The other SE panel had the ground wire exiting itself and going into the adjacent panel that was grounded at the main.
Aren't these supposed to be two separated ground wires going individually to the main? Or is this acceptable? Can a ground wire be shared with each other?
Massachusetts Certified Home Inspections
"Some cause happiness wherever they go; others, whenever they go."