Could someone tell me historically since when
GFCI on all counter top receptacles have been required,
two small appliance branch circuits for the kitchen counter top receptacles has been required,
the bathroom circuit has been required to be 20A protected,
the bathroom circuit should not have any other outlets
Appreciate any feedback.